Careers Business Ownership Learn How to Avoid These Common Plumbing Mistakes Share PINTEREST Email Print sturti / Getty Images Business Ownership Industries Construction Retail Small Business Restauranting Real Estate Nonprofit Organizations Landlords Import/Export Business Freelancing & Consulting Franchises Food & Beverage Event Planning eBay E-commerce Operations & Success Becoming an Owner By Juan Rodriguez Juan Rodriguez LinkedIn University of Puerto Rico DeVry University Juan Rodriguez is a former writer with The Balance who covered large-scale construction. He is an engineer with experience managing and overseeing large civil works construction. Learn about our Editorial Process Updated on 02/04/20 Now that you are ready to start working as a plumber, you may have noticed you need to improve in certain areas. Plumbing is relatively easy if you know what you are doing and if you follow building code regulations. Most jurisdictions follow Uniform Plumbing Code requirements for pipe sizes, but each jurisdiction may have additions or deletions to the code or only use a specific year of the code. This article presents some of the most common mistakes plumbing contractors might run into when doing their work. Problems With Vents and Traps It is easily overlooked that basement fixtures need to have an appropriate vent. Sometimes it is easy to combine vents, but you might want to check your local or state building code. Also, it is also important to add a vent to very trap. When there is no trap, water can be siphoned out, leaving the trap dry and useless. Do not use an S-trap for the sink drain; a P-trap is the right one for this application. Inadequate Slope Too much slope is never good. If you think that having a higher slope will make things easier, think again. A high slope means that liquids will move faster than solid, leaving solid behinds causing major issues later during normal operations. Ideally, 1/4 inch per feet should be enough. Too Many Are Too Many Although some fixtures could have a combined vent, building codes regulate the number of fixtures added to a common vent. The most common error is when more than 24 fixture units are combined on a two-inch vent pipe. Inadequate Plumbing Cleanouts There are many times that the cleanouts are located just in the wrong location. It is important to have the required clearance in order to service the line when it gets clogged. Cleanouts are not required by the code above the first floor but you might want to consider depending on how the line was designed to add some clean out just to facilitate servicing the line. Cleanouts are required at the base of each sanitary stack, on horizontal branches that are 100 feet apart, when the change of direction of the line exceeds 45 degrees or within 10 feet of connection between the main drain and the sewer. Space Around Toilets Be sure to have enough clearance to move around. The toilet must be at least 15 inches from the sidewall and at least 18 inches from the wall in front of the equipment. Lavatories must also be located at least 18 inches from the front wall. Plumbing Pressure Relief Valve Problems Water heaters are equipped with pressure and temperature relief valves that will release pressure when there is a continuous rise in temperature and pressure. The drain line must be a full-size pipe, slope to drain without valves between the drain and the outlet. The fitting located at the end of the line, must not contain any thread and distance from the floor drain shall be carefully observed. Matching Pipes Choosing the wrong pipes can lead to serious problems. A galvanized metal pipe cannot be connected to a copper pipe, as these materials will interact with each other, and will corrode very quickly. You might want to use some sort of brass of another type of fitting suitable to connect these lines. Mind Your Ts and Ys Calculate the number of sanitary T-inlets, combination Y-inlets or 1/8-inch bend inlets that tie into a stack on the drain system to determine the maximum number of fixture units that can be on one stack. Review the "Maximum Number of Fixture Units on One Stack" table in your plumbing codebook.